Problem: Water splashes from fixture.
Cause: Control stop is open wider than necessary.
Solution: Adjust control stop for desired delivery of water volume.
Cause: Water saver/conventional diaphragm assembly is installed on low consumption fixture or closet diaphragm assembly is installed on urinal fixture.
Solution: Determine the required flush volume (see label on valve or markings on fixture). Replace diaphragm assembly or relief valve for appropriate flush volume of fixture.